Underlying Problems: Significant deterioration in source water quality Underlying Problems: No disinfection Underlying Problems: or inadequate disinfection or disinfection residuals Underlying Problems: Unapproved source Underlying Problems: Bacteria presence in most recent sample submission. Recent history of repeat Boil Water Notifications. Steps Taken to Remedy: Engage Facility Emergency Response Plan. Compliance with Source Water Approval dated Feb.27 2018. Facility Manager to post Notification Warning Signs. Corrective Actions Remaining: 3/10/19: Notification removal will be a function of confirming consecutive negative re-sampling results and a satisfactory system review by the District EHO
21/10/19: Operator unable to submit follow-up samples on October 8 and 15 due to bad weather. Facility now closed for the season and water system shut-down. Samples to be submitted prior to next year's operating season (i.e., April 2020) following start-up of this water supply system, which should include a disinfection of the storage tanks and distribution system. Emailed operator to propose this course of action for addressing this BWN.
23/10/19: Operator agreed with proposed course of action. No actions required until April 2020.