Underlying Problems: Insufficient treatment or disinfection residual
Underlying Problems: Water treatment equipment failure
Steps Taken to Remedy: Initiate BWN, notify users. Have a professional shock chlorinate distribution system and equipment, submit microbiological resamples for sites with adverse results, ensure 0.2 ppm.
Corrective Actions Remaining: To be determined
Facility History: Click on an inspection link below to see additional details.