|Inspection date:||October 06, 2011|
This facility was given a low hazard rating.
More information on hazard ratings.
A summary of the violations found during the inspection are listed below.
|Code||Description / Observation / Corrective Action|
|317|| Inadequate or improper construction of water works|
Observation: There were signs of mouse droppings in and around Pumphouse #1.
Corrective Action: Replace rubber stripping under door to prevent pest access. Place traps + prevent continues harbourage and clean area. (This is a previous inspection item)
|320|| Other (specify below)|
Observation: Health Authority has not received and "Emergency Response Plan" or a community flushing maintenance program.
Corrective Action: District of Stewart has confirmed that a draft of these plans will be in place by November, 2011.