|Inspection date:||April 08, 2004|
This facility was given a low hazard rating.
More information on hazard ratings.
A summary of the violations found during the inspection are listed below.
|Code||Description / Observation / Corrective Action|
|316|| Source unprotected and subject to contamination|
Observation: The lid on the well does not appear to be fly-tight.
Corrective Action: A fly-tight well cover is essential to ensure that groundwater is not contaminated by entry of insects or small rodents. Suggest using fly-screen or foam tape to improve the seal.
|317|| Inadequate or improper construction of water works|
Observation: Grade is not mounded up to the well casing.
Corrective Action: It is important to slope impermeable soil (clay-type soil) away from the well casing so as to prevent contaminated surface waters from reaching the casing and flowing down the outside of the casing and entering the well. This is a special concern during spring snowmelt, heavy rain, or during a flood threat.