|Inspection date:||October 05, 2011|
|Number of critical violations:||0|
|Number of non-critical violations:||1|
This facility was given a low hazard rating.
More information on hazard ratings.
A summary of the violations found during the inspection are listed below.
|317|| Inadequate or improper construction of water works|
Observation: Pump house is not pest proof. Signs of mouse feces within pump house. Well head located outside of pump house.
Corrective Action: Clean pump house and secure building to prevent access of pests.