|Inspection date:||August 25, 2010|
|Number of critical violations:||0|
|Number of non-critical violations:||1|
This facility was given a low hazard rating.
More information on hazard ratings.
A summary of the violations found during the inspection are listed below.
|316|| Source unprotected and subject to contamination|
Observation: Pump house not locked and secured at time of inspection
Corrective Action: Lock pump house to ensure that source is protected from unauthorized visitors.