|Inspection date:||May 29, 2007|
|Number of critical violations:||1|
|Number of non-critical violations:||2|
This facility was given a moderate hazard rating.
More information on hazard ratings.
A summary of the violations found during the inspection are listed below.
|317||Critical Inadequate or improper construction of water works|
Observation: (REPEAT VIOLATION) Well casing is located in a well pit. Well casing was extended, however the well pit was not backfilled. Pipe located near the bottom of the well pit suggests that it may be periodically flooded.
Corrective Action: The area where the well is located may be subject to storm water run off during heavy rainfalls and spring melt, which could infiltrate the well pit and potentially enter the well by flowing down the outside of the casing. The well pit is to be backfilled and sealed with a surface seal (as outlined in the BC Groundwater Protection Regulation) prior to October 31, 2007.
|318|| Inadequate Microbiological Analysis data|
Observation: Bacteriological water sample overdue. The last sample was scheduled to be submitted in June.
Corrective Action: Submit bacteriological samples for testing as soon as reasonably possible.
|319|| Inadequate Chemical Analysis Data|
Observation: According to our files the last physical/chemical analysis of the drinking water was done in 2002.
Corrective Action: Water sample to be submitted to a BC approved laboratory for chemical/physical analysis prior to October 31, 2007 or forward any more recent results to our office.